Critical Emergency Municipal Services Depend
on Backup Power
When Anything Less Than 100% Uptime is Not Acceptable
Citizens count on their local governments to protect and provide them with services: Police, Fire, Emergency Management, Utilities, such as Water and Sewer services, Trash and Recycling collection, Emergency Medical Services (EMS), Public Works (roadway maintenance) and more. And those in the administration of a municipality coordinate and oversee these services at a high level, and all need to be informed, engaged and in communication with those in wide ranging facilities and those individuals in the field at all times. But when the SHTF, such as a hurricane emergency, snow or ice emergency, or other emergency that involves a loss of primary power, a municipality loses more than just the lights. The electrical power operates critical emergency services such as communications infrastructure for police, fire and EMS, the water pumps that fill the water towers, keep the sewage lift stations and treatment facilities operating, and runs the fuel pumps that distribute fuel to the emergency vehicles, trucks and other equipment that clear the streets.
These services are all run by professionals and planning for emergency, backup and even redundant electric power sources is second nature. But sometimes things happen that compromises the best laid plans of the smartest people. An extreme example is when hurricane Katrina struck New Orleans in 2005. Plans by First Responders to use cell phones as back up to hand-held radios fell flat when the cell phone network went down, mostly lacking any backup power source.
Much the same, having a backup power generator, but not having a Fuel Management Plan can result in critical mission applications faltering. It is not all that unusual for fuel to remain in storage tanks for over a year. Although service of lubricants, filters and thirty minute test runs of the generator may be undertaken at regular intervals, when the power is needed for an extended period and must operate at a continuous and maximum load, filters can quickly become clogged and engines will not start if the unseen fuel in the storage tank has taken on baggage in the form of microbial contamination and degradation due to instability.
Our experience has shown that fuel problems cause about 70% of all diesel engine failures. And microbial growth in fuel storage tanks and other degradation of diesel fuel’s stability contributes to 90% of those fuel problems. Why understanding and addressing fuel storage problems is critical to the management of any municipality is clear.
Unintended Consequences of Governmental Mandates
Before 2007, when the Environmental Protection Agency (EPA) mandated a change to Ultra Low Sulfur Diesel (ULSD) in on-road applications, diesel fuel contained 500 ppm of sulfur, providing two positive effects. Sulfur was a lubricant for seals in the fuel injectors and injector pumps. Most diesel engines built prior to the year 2000 relied heavily on this lubrication. Current formulations that include a blend of bio-diesel has helped the lubrications situation, but has presented other problems (see below). Also, sulfur acts as a natural biocide that helps prevent microbial growth in diesel fuel tanks. Removing the sulfur makes the diesel fuel much less resistant to fuel microbes (fungus, mold, and bacteria). Since 2014, on road and off road uses now must use ULSD.
Diesel Fuel Shelf Life
According to Caterpillar, today’s ULSD has a shelf life, even when all basic fuel storage maintenance practices are followed by the distributor, of one year beginning when the diesel fuel leaves the producer, and six months for bio-diesel and blended bio-diesel. At temperatures above 86 deg. F (30 deg. C), diesel and bio-diesel fuel storage life is cut in half.
Engine Preventative Maintenance is an important part of a periodic engine maintenance program that is common in all major industries today, but fuel condition is often taken for granted. Many of today’s maintenance personnel have many years of experience, but until changes were regulated to diesel fuel within the past decade and technology advances in diesel engines were introduced, these maintenance professionals were never presented with the problems we are experiencing today with diesel fuel. With today’s advances in design and engineering of diesel engines and the critical requirements that equipment have longer life cycles and near 100% uptime, Fuel Management, as a component of engine preventative maintenance, can no longer be ignored. It is now just as important as changing the oil and ensuring the batteries are charged.
Emergency power installations are especially susceptible to unexpected interruptions due to fuel related issues. Periodic generator tests-runs are too short to determine if fuel quality is adequate for the demands of continuous, full-load operation. In fact, generator test runs have been found to significantly accelerate the fuel polymerization and degradation process by returning fuel that has been compromised by heat and pressure in the engine fuel injector system back to the tank. Thirty minute tests, often performed every month, create the environment in the tank for problems to grow. After extended periods of testing, sometimes years, without the extended full load, operation under full load is interrupted in just a short time by clogged filters.
Modern HPCR Contributes to Fuel Breakdown
In addition, Cat contends that diesel fuels can deteriorate rapidly when fuel is “stressed”. The high pressure (in excess of 30,000 psi) and high temperatures (fuel is used as a coolant for high-pressure fuel injection systems) of today’s engines incorporating High Pressure Common Rail (HPCR) fuel systems results in the fuel enduring these stresses repeatedly as fuel is recirculated back to the fuel tank, causing much of the fuel degradation. Gums and resins that occur in diesel fuel under these stressful conditions are the result of dissolved oxidation products in the fuel that do not evaporate easily and do not burn cleanly. Excessive gum in the fuel will coat the inside of fuel lines, pumps and injectors and interferes with the close tolerances of the moving parts of fuel systems (Caterpillar’s publication SEBU6251-17 “Cat Commercial Diesel Engine Fluids Recommendations”, Page 45).
As a separate issue, water commonly accumulates in stored fuel and is the most damaging contaminant to diesel fuel and the primary catalyst to additional fuel breakdown. Although some water can be added with a fuel fill, much more common is moisture being introduced through a tank vent as air is drawn in to replace used fuel. Temperature changes of as little as seven degrees (see heated fuel above) cause droplets to form on fuel tank walls and accumulate in the bottom of the tank. Above ground fuel tanks have wide temperature variances daily, and the expansion and contraction of the fuel inside the tank draws air in, and pushes air out as it “breathes” with this expansion and contraction of the fuel.
Water is the required component to microbial habitat and growth, and as air is drawn into the tank, so is fungal and other microbial growth. These little critters live in the water, and feed off the components of, and additives in, the fuel. The reproduction process of these microbes produce a black, slimy organic material sometimes seen floating in diesel fuel and on fuel filters (sometimes mistakenly identified as algae). The microbes are too small to filter out, but this black, slimy material shortens filter life, sometimes to minutes instead of hundreds of hours.
Uncontrolled microbial growth creates acids that can corrode the fuel tank, fuel systems and injectors. The water in tank bottoms should be periodically tested for pH. Normal pH for Diesel fuel is between 5.5 and 8.0. A reading of below 5.5 is an indicator there could be a problem. Investigations of serious corrosion problems have disclosed fuel pH measured as low as 2.5.
Today’s Problems Started Six to Nine Months Ago
This situation does not happen overnight. Many maintenance managers will blame a fuel fill and complain to the fuel distributor, but this situation can take six and even nine months to develop to where the slime becomes problematic. The fuel distributor recommends a biocide additive. The problem is that a biocide will shock the organic growth in a tank creating a grit in the tank bottom akin to sand. This debris is then stirred up every time fuel is added to the tank and drawn into the fuel system, further clogging filters. Treating the symptom instead of the real cause of the problem, in this instance, results in creating an additional problem. And with all likelihood, the added biocide becomes diluted and less effective, cannot penetrate the slime and other organic build-up on the tank walls and bottom, and does not eradicate 100% of the microbial growth. And so the cycle begins again.
Natural Fuel Breakdown
Another problem less recognized by the municipal maintenance personnel is the process involving the agglomeration of asphaltenes, a component of diesel fuel, in clogging fuel filters. Asphaltenes are present in all diesel fuel as a function of the process of refining crude oil, are less than 2 microns in size and suspended in the diesel fuel. But stored fuel allows the asphaltene time to form clusters, and as these clusters grow in size, and achieve sizes of 100-200 microns, the fuel begins to appear dark, sometimes black, and filters become black and clogged with these clusters of asphaltenes (see accompanying before-and-after pictures). In storage tanks, they can gain size and weight and drop to the tank bottom adding to the tank sludge in the tank bottom. Inspections of tank bottoms often disclose an appearance of being painted with roofing tar. This is the accumulated asphaltenes.
Eventual Fuel Injector Failure
Fuel injector nozzle holes generally have two failure conditions, which result in a partial functional failure of a fuel injector. These two conditions are blockage, caused by the contaminants in the fuel discussed above, and erosion of the injector ports from the acids formed by the microbial contamination. These conditions lead to fuel non-atomization and leakage of fuel onto the piston crown. The degraded fuel spray pattern results in carbon buildup on injectors, valves and the piston as a result of larger droplets of fuel not fully burning. Leaked fuel results in an increase in piston crown temperature, which can cause the crown to deform or melt, resulting in engine failure. As this may only occur in one cylinder, even an experienced operator or mechanic may not properly diagnose this problem before total engine failure occurs.
Diesel Fuel Cleanliness Requirements
Diesel fuel cleanliness is the ultimate goal. For a more complete understanding of fuel cleanliness and how that term is defined, see the Diesel Fuel and Injector Failure article on this web site.
Caterpillar, like most engine makers, recommends a final filter rated at 4 microns and the use of fuel with an ISO Cleanliness (ISO4406:1999) of ISO 18/16/13. This level of filtration is assumed to allow injectors and other fuel system components to live happy, long lives as the tolerances in injectors are in the 4 to 5 micron range. But the reality is this final filter should not be your first line of defense against nasty fuel. Even with a primary filter rated at 10 microns that may double as a water separator, it is not wise to put a lot of faith in a belief that the fuel is not-so-bad so as to overpower the engine manufacturer’s safeguards. Keep in mind that filters do not stop the acids, and the gums and resins can still get through a 4 micron filter to wreak havoc on your pocketbook.
Caterpillar, as will all engine manufacturers, set standards and make recommendations for a reason. If there should be a failure of components in the fuel system within the warranty period, it is not unheard of for the servicing dealer to check the fuel. If fuel being sourced from the storage tank for use in the generator is not within recommended standards (ISO Cleanliness), warranty claims could be denied.
Diesel fuel that is maintained in a condition as close to “refined” as possible will out perform fuel that is under, or poorly, maintained. In order to achieve optimal fuel quality, the contaminants in fuel must be filtered out, water must be separated and removed, and the fuel must be conditioned. This process of filtration, separation, and conditioning (commonly referred to as the Fuel Polishing process) is the foundation for achieving, and maintaining, the quality of fuel necessary for ultimate reliability. Review the article about Diesel Fuel Polishing, as what some folks call “fuel polishing” is really only filtering the fuel after the use of a biocide. Returning fuel to its clear and bright condition and restoring optimal fuel quality requires an LG-X Series Fuel Conditioner.
The Importance of Fuel Conditioning
MTC X Cart Mounted
Mobile Tank Cleaning System
Although filtration and de-watering is critical, fuel conditioning is paramount. You cannot filter microbes out of fuel, and the asphaltene agglomeration will not be reversed without the use of the Fuel Conditioner. We does not recommend the use of biocides. The Fuel Conditioner works on microbes at the cellular level to prevent reproduction, the cause of the slime (see Learn More About Magnetic Fuel Conditioning). The Fuel Conditioner also breaks down the asphaltene clusters, and with the help of AFC Series Diesel Fuel Catalyst, dissolves the accumulated material on the tank bottom. Use of the AFC Series AFC-705 (pre-2007 engines) or AFC-710 (Tier 4 compliant) Diesel Fuel Catalyst, Stabilizer and Tank Cleaning Additive is recommended to loosens the organic debris from the walls of the tanks, placing the organic material in solution and allowing the Fuel Conditioner to do its job. The process of returning the fuel to a clear and bright condition is key to returning the combustibility of the fuel that was lost to degradation.
The Fuel Management Plan
We recommend you establish a Fuel Management Plan that allows the manufacturer’s filters to be the last line of defense instead of the only line of defense. Place protections in front of those filters by establishing a Fuel Management Plan that keeps your diesel fuel water free, clear, bright, and providing optimal performance. The MTC Series Mobil Cart Mounted Tank Cleaning Systems are examples of cart mounted Tank Cleaning and Fuel Conditioning Systems that will provide for a single unit that can manage dozens of fuel tanks in numerous locals spread around your town. Using this type of mobile unit only once per year on each generator set in most locals (in some locals, depending on temperatures, humidity and other factors, treatments more than once per year may be necessary), will assure that your fuel is in optimal condition, clear and bright, and ready to go to work for you on a moments notice. Larger diesel fuel tanks used for distribution may be better served with a dedicated STS Series Advanced Automated Fuel Management System that will automatically, at predetermined times, clean and filter the storage tank.
Reduced Operating Costs
Your generator unit’s filters will last longer and your engines will enjoy the longevity that you expect from them. As a bonus, the same MTC Series Mobil Tank Cleaning System can also be used on various other equipment and diesel vehicles that are part of your equipment inventory to clean all fuel storage tanks and equipment tanks, and polish the fuel so you are ready when the power goes out and your community is in need.
Now that you have decided to institute a Fuel Management Plan for your municipal operations, there is work to do. Consider the following as the basis for your Fuel Management Program to further assure that your equipment will run when it is needed most and repair costs are under control:
- Place in service a Tank Cleaning System appropriate to your operations and capable of performing a complete tank cleaning and fuel conditioning on each generator unit in service at lease once per year, and evaluate what other critical equipment needs to be included in your Fuel Management Plan.
- Use AFC Series Broad Spectrum Fuel Catalyst Ultra Concentrate AFC-705 or AFC-710 every six months to enhance the breakdown and removal of sludge, slime, gums, resins, and bio-film from tank walls and baffles that are difficult to access and normal fluid flow does not break loose. Having this unique fuel additive present when fueling downstream equipment also assures that these downstream tanks are being cleaned in the normal course of operations.
- Periodically use a Fluid Sampler or a hand Fuel Sample Pump to take samples of your fuel from each storage tank and critical equipment for in-house testing for acidity (pH) and use Liqui-Cult Fuel Test Kits to perform initial testing for microbial contamination. If initial tests indicate fuel problems, utilize laboratory analysis to evaluate the condition of your fuel to assure your fuel supplier is providing fuel that meets the specification of the engine manufacturer you depend on to keep your equipment running.
- Use Kolor Kut Water Finding Paste at least every 60-days to monitor the accumulation of water in your storage and equipment fuel tanks.
- Install Desiccant Breathers on all your fuel storage tanks to help prevent moisture from entering your tanks through the vent as fuel is consumed?
- Use Water Eliminators in each storage and equipment fuel tank to capture water and remove it before it can cause problems with engine operations or seasonally prevent water from freezing in fuel lines?
With only moderate effort, you can be assured that your diesel fuel will provide optimal performance and enjoy the expected life of your fuel filters, diesel engine and engine components.